OMU series three phase oil-immersed metering units (hereinafter referred to as metering unit) applies to the rated voltage of 11kV and 33kV,rated frequency of 50-60Hz for power measurement with the three phase three wire and three phase four wire AC network, by the combination of CT/PT together. This product meet the std IEC61869-1.2&3
l Ambient temperature: -40ºC~+85ºC, day temperature difference: 25ºC;
l Altitude:≤3000m area;
l Wind speed no exceeds 35m/s;
l No normally intensity vibration
l No intensity erosion gas, medium place (for example acid, alkali, smother eg.)
l Pollution class: IV class;
l Charge temperature -40ºC~+85ºC.
Note: * Beyond those services condition should enquiry to manufacturer technical dept during order
l Various irrigation and drainage stations in rural enterprises, township enterprises, processing plants, small and medium factories, mines, transportation, public institutions as well as forestry, energy metering infrastructure temporarily located on site high-voltage transmission lines power station.
l The product consists of a combination of transformers and metering meter box composition, combined transformer consists of three voltage transformers and three current transformers are assembled together.
l Voltage transformer iron outer core is to use high-quality cold-rolled silicon steel sheet orientation is piled up in the column for the multi-step shape in a column equipped with primary and secondary coils.
l Current transformer core is iron formula, with high-quality cold-rolled silicon steel sheet orientation is piled up in the legs of equipped with primary and secondary coils.
l Porcelain jacket by conductive bars will lead to a supply voltage, current transformers with wiring. Voltage and current transformers are fixed on the pallet, the pallet support bar by lifting the lid on, and immersed in transformer oil.
l High-voltage lead casing, the second casing mounted on the lead cover, tank side with the drain plug grounding bolts.
Voltage transformer (VT’s)
Although less common, where a three phase voltage transformer is supplied it shall meet the requirements of AS1243 – 1982. For a Three phase Voltage Transformer (VT), Star/star ratios of either: • (11,000 /√3) / (110 /√3) Volt • (22,000 /√3) / (110 /√3) Volt • (33,000 /√3) / (110 /√3) Volt Rated output: 25 VA per phase Accuracy Class: 0.5M Performance: Category B Rated voltage factor 1.1 continuous and 1.5 for 30 seconds.
Current transformer (CT’s)
The current transformers shall meet the requirements of AS 60044.1- 2007. They can be included with the Voltage Transformer as part of a metering unit, or installed in each phase in a high voltage metering chamber. The following Table provides the preferred ratios and accuracy class for each supply voltage for loads within the specified load range (kVA). Single ratio CTs may also be used where they meet the present and future load of the customer, typically though alternate ratios and specifications must be agreed with the Metering Provider prior to installation.
The rated output on any CT shall be a minimum of 5 VA on the lowest tap setting. If the load range is outside the above table then the Metering Provider needs to be consulted for the size of the CT’s required. For loads less than 50% of the lowest tap or are intermittent or seasonal in nature (i.e. Wind Generation, Sugar Mills, Cotton Gins etc.) accuracy Class 0.5S CT’s are required to be installed.